STANDARDS FOR EQUIPMENT AND MATERIALS All electrical installations shall comply with the requirements of the Regulations. Relevant DEWA’s. DEWA’s requirements for electric installations in order to safeguard to the sixteenth edition of the IEE Wiring Regulations, British Stan-. The Electricity Wiring Regulations (Third Edition). 3. The Regulation and Dubai Electricity and Water Authority (DEWA). Dubai Municipality.
|Published (Last):||21 November 2009|
|PDF File Size:||5.39 Mb|
|ePub File Size:||4.83 Mb|
|Price:||Free* [*Free Regsitration Required]|
Current carrying capacity of a conductor: An allowance for diversity may be permitted where appropriate. Suitable correction factor shall be applied to the corresponding current carrying capacity based on number of circuits and dwea of installation touching or spaced b. The industrial plugs and socket —outlets shall comply with BS and shall be with switch, integrally built in or attached to it. The frequency of periodic inspection and testing of an installation shall be determined by the type of installation, its use and operation, the frequency of maintenance and the external influences to which it is subjected.
Activity code — Electrical Fitting Contracting. Flexible steel conduits and fittings shall comply with BS Part 1. Rated primary current and secondary current. No socket-outlet shall retulations mounted within deea meters of any water tap, wash basin or sink in a kitchen.
The components of the assembly may be electromechanical or electronic. Three CLTs shall be provided for each metering.
Prior approval shall be obtained from DEWA on every such application. Back up power supply — Data Centers Uninterruptible Power Systems and related electrical systems for Data Centers An essential part of any business contingency plan, installatiobs having a backup power supply. Minimum 4 years as professional with documented experience in Design and Installation of electrical systems e.
Please enter your email address. Our routine Capacitor P. The rating and type of socket-outlets with plugs provided shall be selected to suit individual applications and shall not be interchangeable for different current ratings.
Metering by means of Current Transformers CTs shall be installed where the circuit breaker rating at the point of supply is Amps and above. All distribution boards shall be installed flush or surface mounted at a height not exceeding 2 meters to eewa top of the distribution board from the finished floor level. The armoured cables, for underground installation shall normally be laid at 90 cm below the ground level and provided with a layer of at least 15cm impervious soil around.
DEWA REGULATIONS FOR ELECTRICAL INSTALLATIONS –
Power Supply Installations Electrical wiring based on power demand on the circuit and installation of cabling and associated devices such as switches, distribution boards, sockets and light fittings in a structure As per DEWA regulations. A protective conductor providing equipotential bonding.
electrifal Assess initial demand with safe diversity and anticipated demand in future, if any, as applicable to individual circuits, for selection of cable size, breakers rating, etc. Rated frequency and primary maximum voltage Accuracy class.
We will certainly refer youto our own clients. A part providing a defined degree of protection against contact with live parts from any usual direction of access. Connecting of the exposed-conductive-parts of an installation to the main earthing terminal of that installation.
We welcome the opportunity to align ourselves with like-minded contractors.
DEWA issues Regulations for Electrical Installations 2017 booklet
Cables are elecrrical to be bunched when two or more are contained within a single conduit, duct, instsllations, or trunking or, if not enclosed, are not separated from each other by a specified distance.
V Distribution and tariff KWh metering Refer to Appendix-5, for symbols and relevant technical specifications. Where three or more units are installed they shall be balanced as nearly possible lover a three phase supply. Fluorescent lamp assessed as 1. A luminaire track system is not regarded as a socket-outlet system.
Where a residential premise is supplied with a three phase supply as far as possible, the light fittings, socket outlets, water heaters, cookers and other single phase apparatus installed rgeulations any room shall not be connected to more than one phase.
Suitable corrector factor shall be applied to the corresponding current carrying capacity based on the number of cables and the method of installation touching or spaced. Resistance area for an earth electrode only.
Electrical connection maintaining various exposed-conductive parts and extraneous conductive-parts at substantially the same potential. Concept electrical design and budgeting Detailed design and approvals Installation, Service and maintenance LLE is a DEWA Approved Contractor and ensures that all installations are carried out to conform to the latest legislation.
The actual voltage of the installation may differ from the nominal value by a quantity within normal tolerances. Each distribution board shall incorporate means for isolation of mains supply in the form of either circuit breaker or incomer isolator as applicable.
Starters shall be provided with overload relays of the thermal type with automatic compensations for variation in ambient temperature between 2. Suitable expansion couplers shall be provided in all trunking and conduit runs at the expansion joints in the building structure and at regular intervals in all runs exceeding 7 meters in length or as recommended by the manufacturer. By maintaining plant and equipment in the optimum condition, their life should be maximized, and energy costs reduced.
From the complicated process of applying for an additional load at DEWA, to execution, to completion, and handing over – everything was done within time and more importantly within budget. As per DEWA regulations and the environment in which the wiring must operate. Suitable non-conductive material enclosing, surrounding or supporting a conductor. Polyvinyl Chloride Compound complying with BS Guidelines on requirement of PF improvements is also given in Section 8. Where more than one incoming supply is available, in any premises, each ‘Main Switch’ shall be marked to indicate which installation or section of the installation it controls.
Cable trunking may be used for housing single core PVC cables at special situations, where installation of conduits is difficult due to space limitations. A consumer’s load is not allowed to cause deviations of the voltage characteristics other than those allowed in European Standard ENNov.
Adequate mechanical and electrical interlock between the incomer circuit breakers or isolators of both generator and DEWA supplies shall be provided. C between conductors and Earth.
A current demand of 15 A shall be assumed for each 15 A switched socket-outlet circuit. All bus bar risers installed for electrical distribution in high rise buildings and other electricall installations shall incorporate an adequately sized ‘ECC’ either integrally with in or run separately along the riser.
Supply and installation of pendant lights, downlights, IP rated lights for offices, bathrooms regjlations wet rooms, track lighting, spotlights, LED lighting, emergency lighting etc. The heater shall incorporate an integral earthing terminal adjacent to the phase and neutral terminals.